### Overview

The “Ground fault protection for high resistance ground faults in grounded-neutral systems” detects high-resistance ground faults in electric equipment in grounded systems and short circuits phase selectively.

For more detailed information on “Ground fault protection for high resistance ground faults in grounded-neutral systems” function, refer to SIPROTEC 5 devices, V8.30 & higher manuals.

To see other supported functions, click here.

#### Structure/Embedding of the Function

### Setting Parameters

#### Setting parameters for Stage with Definite-Time Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:2311:114 | General:Polarization with | V0 + IY or V2 + I2 V0 + IY (neutral pt.) IY (neutral pt.) only V2 + I2 (neg. seq.) zero-sequence power |
V0 + IY or V2 + I2 | |

_:2311:101 | General:Angle forward α | 0 ° to 360 ° | 338 ° | |

_:2311:102 | General:Angle forward β | 0 ° to 360 ° | 122 ° | |

_:2311:103 | General:Min. zero-seq. voltage V0 | 0.150 V to 34.000 V | 1.213 V | |

_:2311:115 | General:Dir.reslt=forw.at V0<min | no yes |
no | |

_:2311:104 | General:Min.3I0 f.increas.dir.sens. | 1 A @ 100 Irated | 0.030 A to 10.000 A | 0.030 A |

5 A @ 100 Irated | 0.15 A to 50.00 A | 0.15 A | ||

1 A @ 50 Irated | 0.030 A to 10.000 A | 0.030 A | ||

5 A @ 50 Irated | 0.15 A to 50.00 A | 0.15 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 0.030 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 0.150 A | ||

_:2311:105 | General:Min. neutral- point curr. IY | 1 A @ 100 Irated | 0.030 A to 10.000 A | 0.050 A |

5 A @ 100 Irated | 0.15 A to 50.00 A | 0.25 A | ||

1 A @ 50 Irated | 0.030 A to 10.000 A | 0.050 A | ||

5 A @ 50 Irated | 0.15 A to 50.00 A | 0.25 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 0.050 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 0.250 A | ||

_:2311:107 | General:Min. neg.-seq. voltage V2 | 0.150 V to 34.000 V | 1.213 V | |

_:2311:106 | General:Min. neg.-seq. current I2 | 1 A @ 100 Irated | 0.030 A to 10.000 A | 0.050 A |

5 A @ 100 Irated | 0.15 A to 50.00 A | 0.25 A | ||

1 A @ 50 Irated | 0.030 A to 10.000 A | 0.050 A | ||

5 A @ 50 Irated | 0.15 A to 50.00 A | 0.25 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 0.050 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 0.250 A | ||

_:2311:108 | General:Compensation angle | 0 ° to 360 ° | 255 ° | |

_:2311:109 | General:Forw. dir. power threshold | 1 A | 0.08 VA to 10.00 VA | 0.52 VA |

5 A | 0.42 VA to 50.00 VA | 2.60 VA | ||

_:2311:116 | General:Dir.corr.at ser.comp.lines | no yes |
no | |

General | ||||

_:4861:1 | Definite-T 1:Mode | off on test |
off | |

_:4861:2 | Definite-T 1:Operate & flt.rec. blocked | no yes |
no | |

_:4861:114 | Definite-T 1:Directional mode | non-directional forward reverse |
non-directional | |

_:4861:8 | Definite-T 1:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:4861:116 | Definite-T 1:Blk. w. inrush curr. detect. | no yes |
no | |

_:4861:131 | Definite-T 1:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:4861:130 | Definite-T 1:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:4861:129 | Definite-T 1:Op.mode at 1p dead time | blocked non-directional |
blocked | |

_:4861:112 | Definite-T 1:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:4861:115 | Definite-T 1:Dynamic settings | no yes |
no | |

_:4861:111 | Definite-T 1:Stabiliz. w. phase current | 0 % to 30 % | 10 % | |

_:4861:3 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:6 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.s: AR off/n.rdy | ||||

_:4861:117 | Definite-T 1:Effect. by AR off/n.ready | no yes |
no | |

_:4861:123 | Definite-T 1:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:4861:118 | Definite-T 1:Effected by AR cycle 1 | no yes |
no | |

_:4861:124 | Definite-T 1:Stage blocked | no yes |
||

_:4861:101 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:106 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: AR cycle 2 | ||||

_:4861:119 | Definite-T 1:Effected by AR cycle 2 | no yes |
no | |

_:4861:125 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:102 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:107 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: AR cycle 3 | ||||

_:4861:120 | Definite-T 1:Effected by AR cycle 3 | no yes |
no | |

_:4861:126 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:103 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:108 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.s: AR cycle>3 | ||||

_:4861:121 | Definite-T 1:Effected by AR cycle gr. 3 | no yes |
no | |

_:4861:127 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:104 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:109 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: bin.input | ||||

_:4861:122 | Definite-T 1:Effected by binary input | no yes |
no | |

_:4861:128 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:105 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4861:110 | Definite-T 1:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

_:4861:140 | Definite-T 1:Blocking by | Setting options depend on configuration | ||

General | ||||

_:4862:1 | Definite-T 2:Mode | off on test |
off | |

_:4862:2 | Definite-T 2:Operate & flt.rec. blocked | no yes |
no | |

_:4862:114 | Definite-T 2:Directional mode | non-directional forward reverse |
non-directional | |

_:4862:8 | Definite-T 2:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:4862:116 | Definite-T 2:Blk. w. inrush curr. detect. | no yes |
no | |

_:4862:131 | Definite-T 2:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:4862:130 | Definite-T 2:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:4862:129 | Definite-T 2:Op.mode at 1p dead time | blocked non-directional |
blocked | |

_:4862:112 | Definite-T 2:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:4862:115 | Definite-T 2:Dynamic settings | no yes |
no | |

_:4862:111 | Definite-T 2:Stabiliz. w. phase current | 0 % to 30 % | 10 % | |

_:4862:3 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:6 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.s: AR off/n.rdy | ||||

_:4862:117 | Definite-T 2:Effect. by AR off/n.ready | no yes |
no | |

_:4862:123 | Definite-T 2:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:4862:118 | Definite-T 2:Effected by AR cycle 1 | no yes |
no | |

_:4862:124 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:101 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:106 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: AR cycle 2 | ||||

_:4862:119 | Definite-T 2:Effected by AR cycle 2 | no yes |
no | |

_:4862:125 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:102 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:107 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: AR cycle 3 | ||||

_:4862:120 | Definite-T 2:Effected by AR cycle 3 | no yes |
no | |

_:4862:126 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:103 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:108 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.s: AR cycle>3 | ||||

_:4862:121 | Definite-T 2:Effected by AR cycle gr. 3 | no yes |
no | |

_:4862:127 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:104 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:109 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

Dyn.set: bin.input | ||||

_:4862:122 | Definite-T 2:Effected by binary input | no yes |
no | |

_:4862:128 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:105 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:4862:110 | Definite-T 2:Operate delay | 0.000 s to 60.000 s | 0.300 s | |

_:4862:140 | Definite-T 2:Blocking by | Setting options depend on configuration | ||

#### Setting parameters for Stage with Inverse-Time Overcurrent Protection According to IEC and ANSI

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | Inverse-T #:Mode | off on test |
off | |

_:2 | Inverse-T #:Operate & flt.rec. blocked | no yes |
no | |

_:115 | Inverse-T #:Directional mode | non-directional forward reverse |
non-directional | |

_:8 | Inverse-T #:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:117 | Inverse-T #:Blk. w. inrush curr. detect. | no yes |
no | |

_:135 | Inverse-T #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:131 | Inverse-T #:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:130 | Inverse-T #:Op.mode at 1p dead time | blocked non-directional |
blocked | |

_:113 | Inverse-T #:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:116 | Inverse-T #:Dynamic settings | no yes |
no | |

_:112 | Inverse-T #:Stabiliz. w. phase current | 0 % to 30 % | 10 % | |

_:3 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:133 | Inverse-T #:Type of char- acter. curve | |||

_:106 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

_:132 | Inverse-T #:Additional time delay | 0.000 s to 60.000 s | 1.200 s | |

_:134 | Inverse-T #:Reset | instantaneous disk emulation |
instantaneous | |

Dyn.s: AR off/n.rdy | ||||

_:118 | Inverse-T #:Effect. by AR off/n.ready | no yes |
no | |

_:124 | Inverse-T #:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:119 | Inverse-T #:Effected by AR cycle 1 | no yes |
no | |

_:125 | Inverse-T #:Stage blocked | no yes |
no | |

_:101 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:107 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: AR cycle 2 | ||||

_:120 | Inverse-T #:Effected by AR cycle 2 | no yes |
no | |

_:126 | Inverse-T #:Stage blocked | no yes |
no | |

_:102 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:108 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: AR cycle 3 | ||||

_:121 | Inverse-T #:Effected by AR cycle 3 | no yes |
no | |

_:127 | Inverse-T #:Stage blocked | no yes |
no | |

_:103 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:109 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.s: AR cycle>3 | ||||

_:122 | Inverse-T #:Effected by AR cycle gr. 3 | no yes |
no | |

_:128 | Inverse-T #:Stage blocked | no yes |
no | |

_:104 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:110 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: bin.input | ||||

_:123 | Inverse-T #:Effected by binary input | no yes |
no | |

_:129 | Inverse-T #:Stage blocked | no yes |
no | |

_:105 | Inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:111 | Inverse-T #:Time dial | 0.05 to 15.00 | 1.00 | |

_:140 | Inverse-T #:Blocking by | Setting options depend on configuration | ||

#### Setting parameters for Stage with Inverse-Time Overcurrent Protection with Logarithmic-Inverse Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | Log.-inv.-T #:Mode | off on test |
off | |

_:2 | Log.-inv.-T #:Operate & flt.rec. blocked | no yes |
no | |

_:118 | Log.-inv.-T #:Directional mode | non-directional forward reverse |
non-directional | |

_:8 | Log.-inv.-T #:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:120 | Log.-inv.-T #:Blk. w. inrush curr. detect. | no yes |
no | |

_:135 | Log.-inv.-T #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:134 | Log.-inv.-T #:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:133 | Log.-inv.-T #:Op.mode at 1p dead time | blocked non-directional |
blocked | |

_:116 | Log.-inv.-T #:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:119 | Log.-inv.-T #:Dynamic settings | no yes |
no | |

_:115 | Log.-inv.-T #:Stabiliz. w. phase current | 0 % to 30 % | 10 % | |

_:3 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:106 | Log.-inv.-T #:Threshold multiplier | 1.00 to 4.00 | 1.10 | |

_:6 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

_:112 | Log.-inv.-T #:Min. time of the curve | 0.000 s to 60.000 s | 1.200 s | |

_:113 | Log.-inv.-T #:Max. time of the curve | 0.000 s to 60.000 s | 5.800 s | |

_:114 | Log.-inv.-T #:Additional time delay | 0.000 s to 60.000 s | 1.200 s | |

Dyn.s: AR off/n.rdy | ||||

_:121 | Log.-inv.-T #:Effect. by AR off/n.ready | no yes |
no | |

_:127 | Log.-inv.-T #:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:122 | Log.-inv.-T #:Effected by AR cycle 1 | no yes |
no | |

_:128 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:101 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:107 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: AR cycle 2 | ||||

_:123 | Log.-inv.-T #:Effected by AR cycle 2 | no yes |
no | |

_:129 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:102 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:108 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: AR cycle 3 | ||||

_:124 | Log.-inv.-T #:Effected by AR cycle 3 | no yes |
||

_:130 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:103 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:109 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.s: AR cycle>3 | ||||

_:125 | Log.-inv.-T #:Effected by AR cycle gr. 3 | no yes |
no | |

_:131 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:104 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:110 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: bin.input | ||||

_:126 | Log.-inv.-T #:Effected by binary input | no yes |
no | |

_:132 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:105 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:111 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

_:140 | Log.-inv.-T #:Blocking by | Setting options depend on configuration | ||

#### Setting parameters for Stage with S0 Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | S0 inverse-T #:Mode | off on test |
off | |

_:2 | S0 inverse-T #:Operate & flt.rec. blocked | no yes |
no | |

_:108 | S0 inverse-T #:Direc- tional mode | non-directional forward reverse |
non-directional | |

_:8 | S0 inverse-T #:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:109 | S0 inverse-T #:Blk. w. inrush curr. detect. | no yes |
no | |

_:112 | S0 inverse-T #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:111 | S0 inverse-T #:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:106 | S0 inverse-T #:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:105 | S0 inverse-T #:Stabiliz. w. phase current |
0 % to 30 % | 10 % | |

_:3 | S0 inverse-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:101 | S0 inverse-T #:Threshold multiplier | 1.00 to 4.00 | 1.10 | |

_:102 | S0 inverse-T #:k-fact. for Sr-character. | 0.000 s to 60.000 s | 0.500 s | |

_:103 | S0 inverse-T #:S ref for Sr-characteristic | 1 A | 0.84 VA to 100.00 VA | 17.32 VA |

5 A | 4.20 VA to 500.00 VA | 86.61 VA | ||

_:104 | S0 inverse-T #:Additional time delay | 0.000 s to 60.000 s | 1.200 s | |

_:140 | S0 inverse-T #:Blocking by | Setting options depend on configuration | ||

#### Setting parameters for Stage with U0 Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

V0 inverse-T # | ||||

_:1 | V0 inverse-T #:Mode | off on test |
off | |

_:2 | V0 inverse-T #:Operate & flt.rec. blocked | no yes |
no | |

_:108 | V0 inverse-T #:Direc- tional mode | non-directional forward reverse |
forward | |

_:8 | V0 inverse-T #:Method of measurement | 1-cycle filter 2-cycle filter |
1-cycle filter | |

_:109 | V0 inverse-T #:Blk. w. inrush curr. detect. | no yes |
no | |

_:113 | V0 inverse-T #:Blk. w. 2nd harm. gnd. det. | no yes |
||

_:111 | V0 inverse-T #:Blocking by prot. pickup | every pickup no pickup |
every pickup | |

_:106 | V0 inverse-T #:Hold mode 1p dead time | 0.000 s to 60.000 s | 0.040 s | |

_:105 | V0 inverse-T #:Stabiliz. w. phase current |
0 % to 30 % | 10 % | |

_:101 | V0 inverse-T #:Threshold 3I0 | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.000 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 5.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.000 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 5.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.000 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 5.000 A | ||

_:102 | V0 inverse-T #:V0> threshold value | 0.300 V to 200.000 V | 1.667 V | |

_:103 | V0 inverse-T #:Min. zero- seq. volt. V0 | 0.000 V to 200.000 V | 0.200 V | |

_:104 | V0 inverse-T #:Time delay directional | 0.00 s to 60.00 s | 0.90 s | |

_:112 | V0 inverse-T #:Time delay non-direct. | 0.00 s to 60.00 s | 1.20 s | |

_:140 | V0 inverse-T #:Blocking by | Setting options depend on configuration | ||