### Overview

The “Directional overcurrent protection ground” function detects short circuits to ground affecting electric equipment. It ensures selective ground-fault detection for parallel lines or transformers with infeed at one end, and also selective ground-fault detection in cable runs with infeed at both ends or in lines connected to form ring topologies.

For more detailed information on “Directional overcurrent protection ground” function, refer to SIPROTEC 5 devices, V8.30 & higher manuals.

To see other supported functions, click here.

#### Structure/Embedding of the Function Directional Overcurrent Protection, Ground – Advanced

#### Structure/Embedding of the Function Directional Overcurrent Protection, Ground – Basic

### Setting Parameters

#### Genereal Setting Parameters

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:2311:9 | General:Measured value | 3I0 calculated IN measured |
IN measured | |

_:2311:101 | General:Min. voltage V0 or V2 | 0.150 V to 20.000 V | 2.000 V | |

_:2311:102 | General:Rotation angle of ref. volt. | -180 ° to 180 ° | -45 ° | |

_:2311:103 | General:Forward section +/- |
0 ° to 90 ° | 88 ° | |

_:2311:104 | General:Polarization with | zero sequence negative sequence |
zero sequence | |

#### Setting Parameters for Stage with Definite-Time Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:4861:1 | Definite-T 1:Mode | off on test |
off | |

_:4861:2 | Definite-T 1:Operate & flt.rec. blocked | no yes |
no | |

_:4861:105 | Definite-T 1:Directional mode | forward reverse |
forward | |

_:4861:8 | Definite-T 1:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:4861:104 | Definite-T 1:Directional comparison | no yes |
no | |

_:4861:106 | Definite-T 1:Release via input signal | no yes |
no | |

_:4861:10 | Definite-T 1:Blk. by meas.-volt. failure | no yes |
yes | |

_:4861:26 | Definite-T 1:Dynamic settings | no yes |
no | |

_:4861:27 | Definite-T 1:Blk. w. inrush curr. detect. | no yes |
no | |

_:4861:121 | Definite-T 1:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:4861:3 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:4 | Definite-T 1:Dropout ratio | 0.90 to 0.99 | 0.95 | |

_:4861:101 | Definite-T 1:Dropout delay | 0.00 s to 60.00 s | 0.00 s | |

_:4861:6 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.s: AR off/n.rdy | ||||

_:4861:28 | Definite-T 1:Effect. by AR off/n.ready | no yes |
no | |

_:4861:35 | Definite-T 1:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:4861:29 | Definite-T 1:Effected by AR cycle 1 | no yes |
no | |

_:4861:36 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:14 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:20 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.set: AR cycle 2 | ||||

_:4861:30 | Definite-T 1:Effected by AR cycle 2 | no yes |
no | |

_:4861:37 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:15 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:21 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.set: AR cycle 3 | ||||

_:4861:31 | Definite-T 1:Effected by AR cycle 3 | no yes |
no | |

_:4861:38 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:16 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:22 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.s: AR cycle>3 | ||||

_:4861:32 | Definite-T 1:Effected by AR cycle gr. 3 | no yes |
no | |

_:4861:39 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:17 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:23 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.s: Cold load PU | ||||

_:4861:33 | Definite-T 1:Effect. b. cold-load pickup | no yes |
no | |

_:4861:40 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:18 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:24 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

Dyn.set: bin.input | ||||

_:4861:34 | Definite-T 1:Effected by binary input | no yes |
no | |

_:4861:41 | Definite-T 1:Stage blocked | no yes |
no | |

_:4861:19 | Definite-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4861:25 | Definite-T 1:Operate delay | 0.00 s to 60.00 s | 0.30 s | |

General | ||||

_:4862:1 | Definite-T 2:Mode | off on test |
off | |

_:4862:2 | Definite-T 2:Operate & flt.rec. blocked | no yes |
no | |

_:4862:105 | Definite-T 2:Directional mode | forward reverse |
forward | |

_:4862:8 | Definite-T 2:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:4862:104 | Definite-T 2:Directional comparison | no yes |
no | |

_:4862:106 | Definite-T 2:Release via input signal | no yes |
no | |

_:4862:10 | Definite-T 2:Blk. by meas.-volt. failure | no yes |
yes | |

_:4862:26 | Definite-T 2:Dynamic settings | no yes |
no | |

_:4862:27 | Definite-T 2:Blk. w. inrush curr. detect. | no yes |
no | |

_:4862:121 | Definite-T 2:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:4862:3 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:4 | Definite-T 2:Dropout ratio | 0.90 to 0.99 | 0.95 | |

_:4862:101 | Definite-T 2:Dropout delay | 0.00 s to 60.00 s | 0.00 s | |

_:4862:6 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.s: AR off/n.rdy | ||||

_:4862:28 | Definite-T 2:Effect. by AR off/n.ready | no yes |
no | |

_:4862:35 | Definite-T 2:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:4862:29 | Definite-T 2:Effected by AR cycle 1 | no yes |
no | |

_:4862:36 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:14 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:20 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.set: AR cycle 2 | ||||

_:4862:30 | Definite-T 2:Effected by AR cycle 2 | no yes |
no | |

_:4862:37 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:15 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:21 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.set: AR cycle 3 | ||||

_:4862:31 | Definite-T 2:Effected by AR cycle 3 | no yes |
no | |

_:4862:38 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:16 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:22 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.s: AR cycle>3 | ||||

_:4862:32 | Definite-T 2:Effected by AR cycle gr. 3 | no yes |
no | |

_:4862:39 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:17 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:23 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.s: Cold load PU | ||||

_:4862:33 | Definite-T 2:Effect. b. cold-load pickup | no yes |
no | |

_:4862:40 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:18 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:24 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

Dyn.set: bin.input | ||||

_:4862:34 | Definite-T 2:Effected by binary input | no yes |
no | |

_:4862:41 | Definite-T 2:Stage blocked | no yes |
no | |

_:4862:19 | Definite-T 2:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4862:25 | Definite-T 2:Operate delay | 0.00 s to 60.00 s | 0.10 s | |

#### Setting Parameters for Stage with Inverse-Time Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:4891:1 | Inverse-T 1:Mode | off on test |
off | |

_:4891:2 | Inverse-T 1:Operate & flt.rec. blocked | no yes |
no | |

_:4891:111 | Inverse-T 1:Directional mode | forward reverse |
forward | |

_:4891:8 | Inverse-T 1:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:4891:110 | Inverse-T 1:Directional comparison | no yes |
no | |

_:4891:112 | Inverse-T 1:Release via input signal | no yes |
no | |

_:4891:10 | Inverse-T 1:Blk. by meas.-volt. failure | no yes |
yes | |

_:4891:26 | Inverse-T 1:Dynamic settings | no yes |
no | |

_:4891:27 | Inverse-T 1:Blk. w. inrush curr. detect. | no yes |
no | |

_:4891:121 | Inverse-T 1:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:4891:3 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:130 | Inverse-T 1:Type of char- acter. curve | |||

_:4891:114 | Inverse-T 1:Min. time of the curve | 0.00 s to 1.00 s | 0.00 s | |

_:4891:131 | Inverse-T 1:Reset | instantaneous disk emulation |
disk emulation | |

_:4891:101 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

_:4891:115 | Inverse-T 1:Additional time delay | 0.00 s to 60.00 s | 0.00 s | |

Dyn.s: AR off/n.rdy | ||||

_:4891:28 | Inverse-T 1:Effect. by AR off/n.ready | no yes |
no | |

_:4891:35 | Inverse-T 1:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:4891:29 | Inverse-T 1:Effected by AR cycle 1 | no yes |
no | |

_:4891:36 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:14 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:102 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

Dyn.set: AR cycle 2 | ||||

_:4891:30 | Inverse-T 1:Effected by AR cycle 2 | no yes |
no | |

_:4891:37 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:15 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:103 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

Dyn.set: AR cycle 3 | ||||

_:4891:31 | Inverse-T 1:Effected by AR cycle 3 | no yes |
no | |

_:4891:38 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:16 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:104 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

Dyn.s: AR cycle>3 | ||||

_:4891:32 | Inverse-T 1:Effected by AR cycle gr. 3 | no yes |
no | |

_:4891:39 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:17 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:105 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

Dyn.s: Cold load PU | ||||

_:4891:33 | Inverse-T 1:Effect. b. cold-load pickup | no yes |
no | |

_:4891:40 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:18 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:106 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

Dyn.set: bin.input | ||||

_:4891:34 | Inverse-T 1:Effected by binary input | no yes |
no | |

_:4891:41 | Inverse-T 1:Stage blocked | no yes |
no | |

_:4891:19 | Inverse-T 1:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:4891:107 | Inverse-T 1:Time dial | 0.00 to 15.00 | 1.00 | |

#### Setting Parameters for Stage with Inverse-Time Overcurrent Protection with Logarithmic-Inverse Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | Log.-inv.-T #:Mode | off on test |
off | |

_:2 | Log.-inv.-T #:Operate & flt.rec. blocked | no yes |
no | |

_:119 | Log.-inv.-T #:Directional mode | forward reverse |
forward | |

_:8 | Log.-inv.-T #:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:118 | Log.-inv.-T #:Directional comparison | no yes |
no | |

_:120 | Log.-inv.-T #:Release via input signal | no yes |
no | |

_:10 | Log.-inv.-T #:Blk. by meas.-volt. failure | no yes |
yes | |

_:26 | Log.-inv.-T #:Dynamic settings | no yes |
no | |

_:27 | Log.-inv.-T #:Blk. w. inrush curr. detect. | no yes |
no | |

_:121 | Log.-inv.-T #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:3 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:6 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

_:113 | Log.-inv.-T #:Min. time of the curve | 0.000 s to 60.000 s | 1.200 s | |

_:114 | Log.-inv.-T #:Max. time of the curve | 0.000 s to 60.000 s | 5.800 s | |

_:116 | Log.-inv.-T #:Threshold multiplier | 1.00 to 4.00 | 1.10 | |

_:115 | Log.-inv.-T #:Additional time delay | 0.000 s to 60.000 s | 0.000 s | |

Dyn.s: AR off/n.rdy | ||||

_:28 | Log.-inv.-T #:Effect. by AR off/n.ready | no yes |
no | |

_:35 | Log.-inv.-T #:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:29 | Log.-inv.-T #:Effected by AR cycle 1 | no yes |
no | |

_:36 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:14 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:107 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: AR cycle 2 | ||||

_:30 | Log.-inv.-T #:Effected by AR cycle 2 | no yes |
no | |

_:37 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:15 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:108 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: AR cycle 3 | ||||

_:31 | Log.-inv.-T #:Effected by AR cycle 3 | no yes |
no | |

_:38 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:16 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:109 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.s: AR cycle>3 | ||||

_:32 | Log.-inv.-T #:Effected by AR cycle gr. 3 | no yes |
no | |

_:39 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:17 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:110 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.s: Cold load PU | ||||

_:33 | Log.-inv.-T #:Effect. b. cold-load pickup | no yes |
no | |

_:40 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:18 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:111 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

Dyn.set: bin.input | ||||

_:34 | Log.-inv.-T #:Effected by binary input | no yes |
no | |

_:41 | Log.-inv.-T #:Stage blocked | no yes |
no | |

_:19 | Log.-inv.-T #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:112 | Log.-inv.-T #:Time dial | 0.000 s to 60.000 s | 1.250 s | |

#### Setting Parameters for Stage with Knee-Point Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | Log.inv.T KP #:Mode | off on test |
off | |

_:2 | Log.inv.T KP #:Operate & flt.rec. blocked | no yes |
no | |

_:108 | Log.inv.T KP #:Direc- tional mode | forward reverse |
forward | |

_:8 | Log.inv.T KP #:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:107 | Log.inv.T KP #:Direc- tional comparison | no yes |
no | |

_:106 | Log.inv.T KP #:Release via input signal | no yes |
no | |

_:10 | Log.inv.T KP #:Blk. by meas.-volt. failure | no yes |
yes | |

_:27 | Log.inv.T KP #:Blk. w. inrush curr. detect. | no yes |
no | |

_:121 | Log.inv.T KP #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:3 | Log.inv.T KP #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:109 | Log.inv.T KP #:Time dial | 0.05 to 1.50 | 0.20 | |

_:101 | Log.inv.T KP #:Knee- point current | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.300 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.300 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.300 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.500 A | ||

_:105 | Log.inv.T KP #:Knee- point time | 0.00 s to 100.00 s | 23.60 s | |

_:102 | Log.inv.T KP #:Current at Min. time | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.500 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.500 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 7.50 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.500 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 7.500 A | ||

_:104 | Log.inv.T KP #:Min. time of the curve | 0.00 s to 30.00 s | 0.80 s | |

_:103 | Log.inv.T KP #:Max. time of the curve | 0.00 s to 200.00 s | 93.00 s | |

#### Setting Parameters for Stage with User-Defined Characteristic Curve

Addr. | Parameter | C | Setting Options | Default Setting |

General | ||||

_:1 | User curve #:Mode | off on test |
off | |

_:2 | User curve #:Operate & flt.rec. blocked | no yes |
no | |

_:113 | User curve #:Directional mode | forward reverse |
forward | |

_:8 | User curve #:Method of measurement | fundamental comp. RMS value |
fundamental comp. | |

_:112 | User curve #:Directional comparison | no yes |
no | |

_:114 | User curve #:Release via input signal | no yes |
no | |

_:10 | User curve #:Blk. by meas.-volt. failure | no yes |
yes | |

_:26 | User curve #:Dynamic settings | no yes |
no | |

_:27 | User curve #:Blk. w. inrush curr. detect. | no yes |
no | |

_:121 | User curve #:Blk. w. 2nd harm. gnd. det. | no yes |
no | |

_:3 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:110 | User curve #:Reset | instantaneous disk emulation |
disk emulation | |

_:101 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.s: AR off/n.rdy | ||||

_:28 | User curve #:Effect. by AR off/n.ready | no yes |
no | |

_:35 | User curve #:Stage blocked | no yes |
no | |

Dyn.set: AR cycle 1 | ||||

_:29 | User curve #:Effected by AR cycle 1 | no yes |
no | |

_:36 | User curve #:Stage blocked | no yes |
no | |

_:14 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:102 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: AR cycle 2 | ||||

_:30 | User curve #:Effected by AR cycle 2 | no yes |
no | |

_:37 | User curve #:Stage blocked | no yes |
no | |

_:15 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:103 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: AR cycle 3 | ||||

_:31 | User curve #:Effected by AR cycle 3 | no yes |
no | |

_:38 | User curve #:Stage blocked | no yes |
no | |

_:16 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:104 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.s: AR cycle>3 | ||||

_:32 | User curve #:Effected by AR cycle gr. 3 | no yes |
no | |

_:39 | User curve #:Stage blocked | no yes |
no | |

_:17 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:105 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.s: Cold load PU | ||||

_:33 | User curve #:Effect. b. cold-load pickup | no yes |
no | |

_:40 | User curve #:Stage blocked | no yes |
no | |

_:18 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:106 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |

Dyn.set: bin.input | ||||

_:34 | User curve #:Effected by binary input | no yes |
no | |

_:41 | User curve #:Stage blocked | no yes |
no | |

_:19 | User curve #:Threshold | 1 A @ 100 Irated | 0.030 A to 35.000 A | 1.200 A |

5 A @ 100 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 50 Irated | 0.030 A to 35.000 A | 1.200 A | ||

5 A @ 50 Irated | 0.15 A to 175.00 A | 6.00 A | ||

1 A @ 1.6 Irated | 0.001 A to 1.600 A | 1.200 A | ||

5 A @ 1.6 Irated | 0.005 A to 8.000 A | 6.000 A | ||

_:107 | User curve #:Time dial | 0.05 to 15.00 | 1.00 | |